Fire System Installation
If you are in need of “Fire System Installation” services then we can help. Here at Current Technologies Ltd. we offer a full selection of services regarding the fire systems. Whether you are in need of a residential, commercial, or industrial fire system; trust our team of experts to provide exceptional results.
Here at Current Technologies Ltd. we have over 20 years of experience with the installation of fire systems for Canadians. We provide ongoing maintenance services to ensure an uninterrupted, continuous and safe working environment with 24 hour emergency service. At Current Technologies Ltd., we promote continued education to our employees ensuring that our clients will receive highly trained professionals for all fire safety installations.
A fire alarm system operates in one of three (or more) states: normal, alarm, and trouble. The state is reported at all times on the alphanumeric display. If the system goes into alarm, the indicating appliances throughout the building go off. These could be very loud horns for some occupancies, or softer chimes in others, such as a nursing home.
The control panel monitors the initiating device circuits at all times for shorts and open wiring by means of the applied DC voltage. The initiating devices are normally open. In the event of a fire they become conductive at close to zero ohms. How, then, is it possible for the control panel to differentiate between a non-alarm state and an open wiring fault? This is accomplished by means of an end-of-line resistor.
The control panel also monitors the functionality of its own wiring and zone cards, and trouble is reported in the display.
Another capability of the fire alarm system is to call out in case of alarm. Two dedicated phone lines are connected, and the system performs test calls periodically in accordance with programmed instructions. If either phone line won’t connect, the system goes into the trouble state, so repairs can be made.
The essence of a fire alarm system, as opposed to individual smoke detectors, even if they are wired to indicate in concert, is that it is supervised from a central location. The whole notion of supervision is critical. It does not mean that a person sits at the console and watches it at all times. What it means is that a supervisory voltage is applied to all circuitry, and current flow is monitored electronically to verify that equipment and wiring are intact.
If the system goes into alarm and won’t silence due to touchpad malfunction, for example, it can be disarmed after the zone is checked for fire by cutting off the power. First, unhook one side of the battery array, then unhook the black-white-green incoming power connector. If a fire alarm system is disabled, maintenance and security personnel should initiate fire patrols throughout the building. The telephone monitoring agency should be informed, and the insurance company contacted to verify that coverage is not voided.